LBNL Report Number
Control software and wireless sensors designed for closed-loop, monitoring and control of IT equipment's inlet air temperatures in datacenters were evaluated and tested while other datacenter cooling best practices were implemented. The controls software and hardware along with each best practice were installed sequentially and evaluated using a measurement and verification procedure between each measure. The results show that the overall project eliminates 475,239 kWh per year, which is 21.3% of the baseline energy consumption of the data center. The total project, including the best practices will save $42,772 per year and cost $134,057 yielding a simple payback of 3.1 years. However, the control system alone eliminates 59.6% of the baseline energy used to move air in the datacenter and 13.6% of the baseline cooling energy, which is 15.2% of the baseline energy consumption (see Project Approach, Task 1, below, for additional information) while keeping temperatures substantially within the limits recommended by ASHRAE. Savings attributed to the control system are $30,564 per year with a cost $56,824 for a simple payback of 1.9 years.